Building Life Cycle Assessment: Marine Drive Residence at The University of British Columbia QuickTime™ and aTIFF (Uncompressed) decompressorare needed to see this picture. Duncan McNicholl CIVL 498C March 27, 2009 QuickTime™ and aTIFF (Uncompressed) decompressorare needed to see this picture.McNicholl 1 Abstract A Life Cycle Assessment of thirteen buildings on UBC campus was conducted as part of a 4th year Civil Engineering undergraduate course in order to assess the environmental impacts generated by the buildings. This paper represents one of the thirteen studies, which was conducted on the Marine Drive Student Residence. Quantity takeoffs were performed using OnScreen Takeoff software on both structural and architectural drawings to generate determine quantities and types of materials used in building construction. These assemblies were then inputted into Athena Environmental Impact Estimator (IE) software to determine the impacts generated by the building. Eight different impact categories were measured using the software and the results for Marine Drive Residence were compared with other residences studied on a per square foot basis, which indicated that this residence has exceptionally high impacts in most categories. Assumptions, input values, and areas of uncertainty have also been outlined in the report and a sensitivity analysis has been conducted to examine the effects of errors and determine how different assemblies correlate to different impact categories. Uncertainties with column and beam assemblies are particularly uncertain. Although calculations were made to model these assemblies as accurately as possible, results seem to be much to high. This may be do to the fact that this study used a version of the IE that was not completely finished being developed (ie. build 51 of version 4). In addition, an energy model was prepared in order to assess heat losses and the potential effects that material upgrades could have to reduce these. McNicholl 2 Table of Contents Abstract............................................................................................................................... 1 Table of Contents................................................................................................................ 2 List of Tables.................................................................................................................. 3 List of Figures..................................................................................................................... 3 1.0 Introduction................................................................................................................... 4 2.0 Goal And Scope ............................................................................................................ 5 2.1 Scope of Study .......................................................................................................... 6 2.2 Tools, Methodology and Data................................................................................... 6 3.0 Building Model ............................................................................................................. 9 3.1 Takeoffs .................................................................................................................... 9 3.1.1 On Grade and Suspended Slabs ......................................................................... 9 3.1.2 Ceiling................................................................................................................ 9 3.1.3 Walls .................................................................................................................. 9 3.1.4 Doors................................................................................................................ 10 3.1.5 Roofs................................................................................................................ 10 3.1.6 Footings............................................................................................................ 10 3.1.7 Column and Beam Assemblies ........................................................................ 10 3.1.8 Windows .......................................................................................................... 10 3.2 Assumptions............................................................................................................ 11 3.2.1 Floor Assumptions........................................................................................... 11 3.2.2 Roof Assumptions............................................................................................ 12 3.2.3 Column and Beam Assumptions...................................................................... 12 3.2.4 Footings and Stairs Assumptions..................................................................... 13 3.2.5 Wall Assumptions............................................................................................ 14 3.3 Bill of Materials ...................................................................................................... 14 4.0 Summary Measures..................................................................................................... 17 4.1 Impact Comparisons ............................................................................................... 20 4.1.1 Primary Energy Consumption.......................................................................... 20 4.1.2 Weighted Resource Use................................................................................... 20 4.1.3 Global Warming Potential ............................................................................... 21 4.1.4 Acidification Potential ..................................................................................... 22 4.1.5 HH Respiratory Effects Potential..................................................................... 23 4.1.6 Eutrophication Potential................................................................................... 23 4.1.7 Ozone Depletion Potential ............................................................................... 24 4.1.8 Smog Potential................................................................................................. 25 4.2 Impacts By Assembly ............................................................................................. 26 4.3 Impact Assessment Uncertainties ........................................................................... 26 5.0 Sensitivity Analysis .................................................................................................... 29 5.1 Gypsum Board Sensitivity ...................................................................................... 29 5.2 Fiberglass Sensitivity.............................................................................................. 30 5.3 Concrete Sensitivity................................................................................................ 32 5.4Rebar, Rod, and Light Sections Sensitivity ............................................................. 33 5.5 Glazing Sensitivity.................................................................................................. 34 6.0 Building Performance ................................................................................................. 35 McNicholl 3 7.0 Conclusions................................................................................................................. 38 Appendix A: EIE Input Tables ......................................................................................... 40 Appendix B: Detailed Assumptions.................................................................................. 51 Appendix C: Aggregated Summary Measures for Residences at UBC............................ 62 List of Tables Table 1-1 - Marine Drive Square Footage Tables............................................ 4 Table 1-2 - Bulding Characteristics....................................................................... 5 Table 4 - Bill of Materials........................................................................................ 16 Table 4 -1 – Marine Drive Summary Measures.............................................. 19 Table 5-1 – Materials Added for Sensitivity Analysis................................... 29 Table 5-2 – Gypsum Board Sensitivity Results............................................... 30 Table 5-3 – Fiberglass Sensitivity Results........................................................ 31 Table 5-4– Concrete Sensitivity Results............................................................ 32 Table 5-5 – Rebar, Rod, and Light Sections Sensitivity Results.............. 33 Table 6-1 – Material R-Values............................................................................... 36 Table 6-2 - Exterior Assembly Areas.................................................................. 36 Table 6-3 – Current and Improved R-Values.................................................. 37 Table 6-4 – Insulation Wastes.............................................................................. 37 Table 6-5 – Embedded Energy ............................................................................. 37 List of Figures Figure 4-1 – Primary Energy Consumption...................................................... 20 Figure 4-2 – Weighted Resource Use................................................................. 21 Figure 4-3 – Global Warming Potential............................................................. 22 Figure 4-4 – Acidification Potential..................................................................... 22 Figure 4-5 – HH Respiratory Effects Potential................................................ 23 Figure 4-6 – Eutrophication Potential ................................................................ 24 Figure 4-7 – Ozone Depletion Potential............................................................ 25 Figure 4-8 – Smog Potential.................................................................................. 25 McNicholl 4 1.0 Introduction Located near Wreck Beach on the west side of UBC's Point Grey Campus, Marine Drive Residence is the newest student residence and exhibits the urban modernity of chic glass high rises. The development has generated some controversy and was halted by Wreck Beach advocates in 2004 who refused to allow the construction of 20 -storey towers that would be in view of nudes on the beach below. The towers were then re-designed to not exceed 18 storeys and construction resumed in 2005. The residence was designed by Hotson Bakker Boniface Haden Associated Architects and structural consultation was provided by Read Jones Christoffersen Consluting Engineers. Information on the total cost of the complex was unavailable. The residence consists of a combination of high-rise towers and lower structures (called podiums) for a total of six buildings, which includes a commons block that does not house students. The units housing students have been completed and are occupied but the commons block is still under construction and is expected to be completed this year. A summary of the buildings and their sizes is presented below. Table 1-1 - Marine Drive Square Footage Tables There is no indication that a Life Cycle Assessment (LCA) has ever been conducted on the Marine Drive Residence before; this report will be the first evaluation of the environmental impacts created by the development. Due to limitations on resources and therefore scope, for the purpose of this study Tower 4 is the only one modeled and this model will be used to represent the entire complex on an impact per square foot basis. Tower 4 is an 18-storey high-rise with a concrete superstructure and a heavily glazed exterior. A summary of the building's composition, which forms the basis for the LCA, is presented in the table below. Building Type Floors Beds Square FtBuilding 1 Tower 18 344 126021Building 2 Podium 5 223 202796Building 3 ( Commons Block) AmenityBuilding 4 Tower 18 405 148119Building 5 Tower 17 368 129297Building 6 Podium 7 294 115120TOTAL = 65 1634 721353omitted from studyMarine Drive Sqaure Footage TablesMcNicholl 5 Table 1-2 - Bulding Characteristics 2.0 Goal And Scope This life cycle analysis (LCA) of the Marine Drive Residence at the University of British Columbia was carried out as an exploratory study to determine the environmental impact of it’s design. The residence consists of five residence buildings, which are referred to collectively as Marine Drive Residence in this report. This LCA of the Marine Drive Residence is also part of a series of twelve others being carried out simultaneously on respective buildings at UBC with the same goal and scope. The main outcomes of this LCA study are the establishment of a materials inventory and environmental impact references for the Marine Drive Residence. An exemplary application of these references are in the assessment of potential future performance upgrades to the structure and envelope of the Marine Drive Residence. When this study is considered in conjunction with the twelve other UBC building LCA studies, further applications include the possibility of carrying out environmental Building SystemConcrete and structural steel columns supporting concrete suspended slabs Basement: Concrete slab on grade; Ground: combination of Suspended slabs and slabs on grade; All other floors (Floors 2-18): Suspended slabsSpecific Characteristics of Marine Drive Tower 4All windows and curtain walls standard glazedFloors Six and Seven: Inverted Membrane Roofing with aggregate ballast, 4" polyisocyanurate insulation on suspended concrete slab; metal roof with 4" polyisocyanurate insulation and waterproofing membrane; Floor 18 Roof: Inverted Membrane Roofing with aggregate ballast, 4" polyisocyanurate insulation on suspended concrete slab; Membrane Roofing System with 4" polyisocyanurate insulation, vapour barrier on suspended concrete slabWindowsFloorsExterior WallsRoofStructureInterior WallsBasement: Cast in place walls; Ground: Cast in place walls with concrete block cladding and acoustic batt insulation; aluminum framed curtain wall with standard glazing; steel stud exterior walls with commercial steel cladding, acoustic batt insulation; Floors Two, Three, Four, and Five: Cast in place walls with concrete block cladding and acoustic batt insulation; steel stud exterior walls with commercial steel cladding, acoustic batt insulation; All other Floors (Floors 7-18):Cast in place walls with acoustic batt insulation; steel stud exterior walls with commercial steel cladding, acoustic batt insulationBasement: cast in place concrete walls; All Other Floors (Floors Ground-18) : gypsum on steel stud walls (some double thickness) with acoustic batt insulationMcNicholl 6 performance comparisons across UBC buildings over time and between different materials, structural types and building functions. Furthermore, as demonstrated through these potential applications, this Marine Drive Residence LCA can be seen as an essential part of the formation of a powerful tool to help inform the decision making process of policy makers in establishing quantified sustainable development guidelines for future UBC construction, renovation and demolition projects. The intended core audience of this LCA study are those involved in building development related policy making at UBC, such as the Sustainability Office, who are involved in creating policies and frameworks for sustainable development on campus. Other potential audiences include developers, architects, engineers and building owners involved in design planning, as well as external organizations such as governments, private industry and other universities whom may want to learn more or become engaged in performing similar LCA studies within their organizations. 2.1 Scope of Study The product system being studied in this LCA are the structure, envelope and operational energy usage associated with space conditioning of the Marine Drive Residence on a square foot finished floor area of residence building basis. In order to focus on design related impacts, this LCA encompasses a cradle-to-gate scope that includes the raw material extraction, manufacturing of construction materials, and construction of the structure and envelope of the Marine Drive Residence, as well as associated transportation effects throughout. 2.2 Tools, Methodology and Data Two main software tools are to be utilized to complete this LCA study; OnCenter’s OnScreen TakeOff and the Athena Sustainable Materials Institute’s Impact Estimator (IE) for buildings. The study will first undertake the initial stage of a materials quantity takeoff, which involves performing linear, area and count measurements of the building’s structure and envelope. To accomplish this, OnScreen TakeOff version 3.6.2.25 is used, which is a McNicholl 7 software tool designed to perform material takeoffs with increased accuracy and speed in order to enhance the bidding capacity of its users. Using imported digital plans, the program simplifies the calculation and measurement of the takeoff process, while reducing the error associated with these two activities. The measurements generated are formatted into the inputs required for the IE building LCA software to complete the takeoff process. These formatted inputs as well as their associated assumptions can be viewed in Appendixes A and B respectively. Using the formatted takeoff data, version 4.0.51 of the IE software, the only available software capable of meeting the requirements of this study, is used to generate a whole building LCA model for the Marine Drive Residence in the Vancouver region as an MURB rented building type. The IE software is designed to aid the building community in making more environmentally conscious material and design choices. The tool achieves this by applying a set of algorithms to the inputted takeoff data in order to complete the takeoff process and generate a Bill of Materials (BoM). This BoM then utilizes the Athena Life Cycle Inventory (LCI) Database, version 4.6, in order to generate a cradle-to-grave LCI profile for the building. In this study, LCI profile results focus on the manufacturing and transportation of materials and their installation in to the initial structure and envelope assemblies. As this study is a cradle-to-gate assessment, the expected service life of the Marine Drive Residence is set to 1 year, which results in the maintenance, operating energy and end-of-life stages of the building’s life cycle being left outside the scope of assessment. The IE then filters the LCA results through a set of characterization measures based on the mid-point impact assessment methodology developed by the US Environmental Protection Agency (US EPA), the Tool for the Reduction and Assessment of Chemical and other environmental Impacts (TRACI) version 2.2. In order to generate a complete environmental impact profile for the Marine Drive Residence, all of the available TRACI impact assessment categories available in the IE are included in this study, and are listed as; • Global warming potential McNicholl 8 • Acidification potential • Eutrophication potential • Ozone depletion potential • Photochemical smog potential • Human health respiratory effects potential • Weighted raw resource use • Primary energy consumption Using the summary measure results, a sensitivity analysis is then conducted in order to reveal the effect of material changes on the impact profile of the Marine Drive Residence. Finally, using the UBC Residential Environmental Assessment Program (REAP) as a guide, this study then estimates the embodied energy involved in upgrading the insulation and window R-values to REAP standards and calculates the energy payback period of investing in a better performing envelope. The primary sources of data for this LCA are the original architectural and structural drawings from when the Marine Drive Residence was initially constructed in 2005. The assemblies of the building that are modeled include the foundation, columns and beams, floors, walls and roofs, as well as the associated envelope and openings (ie. doors and windows) within each of these assemblies. The decision to omit other building components, such as flooring, electrical aspects, HVAC system, finishing and detailing, etc., are associated with the limitations of available data and the IE software, as well as to minimize the uncertainty of the model. In the analysis of these assemblies, some of the drawings lack sufficient material details, which necessitate the usage of assumptions to complete the modeling of the building in the IE software. Furthermore, there are inherent assumptions made by the IE software in order to generate the BoM and limitations to what it can model, which necessitated further assumptions to be made. These assumptions and limitation will be discussed further as they energy in the Building Model section and, as previously mentioned, all specific input related assumption are contained in the Input Assumptions document in Annex B. McNicholl 9 3.0 Building Model 3.1 Takeoffs Building materials and their quantities were determined by performing quantity takeoff calculations on architectural and structural drawings of Tower 4 using OnCenter’s OnScreen TakeOff software. Both sets of drawings were obtained from the UBC records department on West Mall of the Point Grey Campus. The drawings were then imported into On-Screen Takeoff Pro, a program that performs quantity takeoffs using different conditions to calculate areas, lengths, and counts of different assemblies. The program itself is fairly intuitive and the files associated with the takeoff software are included on the CD included with this document. The names of the assemblies correspond to either a description or their names as specified in the drawings. The names are also identical to the names used in the IE input values spreadsheet (included in the Appendix A). A basic breakdown of how different assemblies were modeled is presented below. In some cases, calculations were involved to transform On-Screen Takeoff values into final input values. A complete list of these calculations is presented for reference in Appendix B. 3.1.1 On Grade and Suspended Slabs Concrete slab areas were calculated using an area condition in On-Screen. In the cases where multiple floors were identical, one floor was modeled as a single assembly and then multiplied by the number of identical floors later on to determine the total area. 3.1.2 Ceiling The ceiling area was calculated using an area condition. This was only done on drawings that specifically indicated extra material use in the ceilings. 3.1.3 Walls Wall lengths were calculated using a linear condition in On-Screen. In the cases where multiple floors were identical, one floor was modeled as a single assembly and then McNicholl 10 multiplied by the number of identical floors later on to determine the total area. On-Screen was only used to determine lengths. Other dimensions such as height and thickness were translated directly from drawings into the IE. 3.1.4 Doors Doors were categorized by type and floor set and then counted using count conditions. In the cases where floors were identical, one floor was modeled as a single assembly and then multiplied by the number of identical floors to determine the total number of doors. 3.1.5 Roofs Roofs were broken down by type as specified by the architectural drawings. Areas were then determined using an area condition. 3.1.6 Footings Count conditions were used to count the total number of columns of each type in the building. Dimensions for the footings were translated directly from structural drawings into the IE and are not included in On-Screen. 3.1.7 Column and Beam Assemblies Takeoffs for columns and beams were determined in a three-step process. First, the total supported column areas were determined using an area condition. Most floors were broken into three conditions in order for areas to be more or less rectangular. The number of columns and beams were then counted using count conditions, although the location of beams was often estimated. These three conditions were then combined to determine IE software inputs. 3.1.8 Windows Windows were counted by type and floor series using count conditions and nomenclature specified in the architectural drawings. In the cases of repeated floors, the number of windows was multiplied by the number of identical floors to determine the final IE inputs. Dimensions for the windows were also entered into On-Screen in order to produce McNicholl 11 a secondary calculation of the cumulative window area. Both the window counts and the total window areas were used to calculate final IE inputs. 3.2 Assumptions The following sections detail the general assumptions that were made in order to model each assembly in the IE. A further detailed breakdown of both the general and assembly specific assumptions can be found in Appendix B. Perhaps the largest assumption made in modeling the environmental impacts of the Marine Drive Residence was the method used to extrapolate impacts determined for a single building to represent the entire complex. Originally, assemblies similar between different buildings were replicated in the IE so that the software would be modeling the entire complex. Only Tower 4 has been modeled in the IE software and the final impacts were then calculated using summary measures on a per square foot basis and then multiplied by the total complex square footage in order to determine the overall impacts. Although this will likely be a reasonably accurate means of modeling the other two towers, which are quite similar, there is significant uncertainty around how effectively this model can be extended to include the two podium buildings. Without drawings of the podium buildings it is difficult to verify any estimated degrees of uncertainty. 3.2.1 Floor Assumptions In consistency with other concrete bodies in the structure, since there is no indication of increased fly ash content, it was assumed that all concrete contained only average concentrations of fly ash. One slight modification was made to the concrete in order to fit IE input fields: the strength of concrete was adjusted from 3500 to 4000 psi. Although this will likely result in a higher overall global warming potential in the model, the magnitude of this increase is unknown and therefore not adjusted for. McNicholl 12 Two other general assumptions were also made due to lack of specific information available from the drawings. No floor envelope specifications were provided and since flooring such as carpeting is beyond the scope of this study, floors were assumed to not have envelopes. The other source of uncertainty is related to floor loading specifications, which were indicated in the structural drawings as having a point load of 2 kips. It is unusual to attribute a point load to a floor area, so this was assumed to translate into a uniform area load of 100 psf in order to fit IE input fields. 3.2.2 Roof Assumptions Similarly to the floors, no unusual concrete fly ash concentrations were specified and loading specifications were also given as point loads, specifically as 0.3 kips. In an attempt to be proportionally consistent with other loading assumptions, 0.3 kips was correlated to 45 psf in the IE software. Also, roof concrete strengths were specified as 3500 psi in structural drawings but had to be rounded up to 4000 to fit IE input fields, likely resulting a slightly increased global warming potential for the overall model. 3.2.3 Column and Beam Assumptions Due to the rigidity of the IE inputs and the non-uniformity of the column assembly within the tower, modeling this part of the structure required the largest assumptions and appears to be the greatest source of error within the model. The Athena Environmental Impact Estimator models column and beam assemblies in a grid format, which assumes that bay areas and spans are uniform. It also places minimum values on bay areas and span lengths and will round up to these minimums if an input value is outside the range. In order to conform to this input format, the number of columns and beams were counted, the supported area was determined, and then transformed mathematically into a rectangular grid where length = 2 x width. (See Appendix B for calculation details) Since no drawings detailing beams were available the location of certain beams had to be assumed; beams were only assumed to exist if the length of a span between two columns exceeded 10 ft. Although all beams and columns counted in the quantity takeoffs are McNicholl 13 represented in the model, the values for supported spans are below the minimum required input value, which means that the software may be rounding up the lengths of beams even if this is not evident in the input fields. If rounding is occurring, span values will be rounded up to approximately 20 ft. This cannot be changed without reducing the value for bay areas, which would result in a value below the valid input range and cause the model to not function. Also, input fields in the IE do not allow for concrete strengths to be specified, only live loads. This may be missing an important component in environmental impacts since the concrete strengths change from 25 MPa to 35 MPa from the top of the structure to the bottom respectively. Since these strengths have a significant affect on greenhouse gas emissions, the assumption that all column strengths are the same may not be valid. 3.2.4 Footings and Stairs Assumptions Concrete fly ash content was again assumed to be average and the concrete strength of 5,333 psi had to be changed to 4,000 psi in order to match available input options for all footings. Again, this rigidity in input format contributed to inaccuracies in greenhouse gas emissions estimated by the model. In some cases, the size of rebar also had to be changed to match available input fields. One point of uncertainty is a lack of information on footing envelopes. Structural drawings specify that some envelope material may be necessary but this decision was to be made at the discretion of geotechnical experts at the time of excavation. For the purposes of this model it was assumed that no footing envelopes existed. There is no input category in the IE that represents stairs. Stairs were modeled as footings in order to have more control over concrete volumes and reinforcement dimensions in the model. McNicholl 14 3.2.5 Wall Assumptions Door types specified in the model have been confirmed through drawings and a site visit but the generic terms used in the IE make it uncertain if doors used in the model are an accurate representation of the actual ones. However, it seems likely that this assumption is a minor one since the type of materials has been confirmed and it is only the volume that remains uncertain. Windows were accounted for by counting the number of each type of assembly and then matching them to the areas specified in the window schedule in the architectural drawings. In cases where the window assembly did not match any detailed in the window schedule, an assumption was made based on size and the number of windows and the new assembly was equated to one specified in the window schedule. A complete breakdown of these assumptions and count for the total number of windows can be referenced in Appendix B. Two more assumptions related to the window assemblies were made when the architect was unable to verify drawing ambiguities. The windows were assumed to be of standard glazing with aluminum frames. There was also limited information about the envelopes of the metal stud walls immediately surrounding the windows. These envelopes were assumed to be the same as the single stud drywall partition envelopes that the metal stud walls join to except with a commercial grade steel exterior cladding. Also, due to a few missing specifics in the architectural drawings, steel studs in drywall partitions were assumed to be light (25 Ga) and acoustic batt insulation was interpreted as fiberglass. 3.3 Bill of Materials The following Bill of Materials (BoM) states the estimated types and quantities of materials used in the construction of Tower 4 of the Marine Drive Residence. This BoM was generated using the IE after all assemblies had been inputted from On-Screen calculations. By doing so, material quantities are slightly higher than takeoff values and also present some slightly different materials. This is because the IE software accounts for waste material generated during construction by estimating typical waste amounts and McNicholl 15 adding this to the total quantities. It also breaks down some assemblies into smaller components that are part of their fabrication or associated with construction such as paper tape. McNicholl 16 Table 3 - Bill of Materials Quantity Unit58.2502 m2423.7181 m222304.11 m2772.4108 m236.3141 m265.0757 m2191.8635 m2397.0517 Tonnes231834 Kg46579.05 m2 (25mm)0.2143 Tonnes2723.986 m2399.8188 m328407.46 m313502.87 Blocks1114.098 m234443.73 Kg882.1856 m2 (25mm)1.8828 Tonnes48.5197 Tonnes16.4079 Tonnes3671.973 m2 (25mm)23.132 Tonnes8.5693 m3751.1945 Kg63.5739 m325.003 Tonnes0.2655 Tonnes0.817 Tonnes0.2418 Tonnes1564.151 Tonnes2.7169 Tonnes7.7807 m33.8268 m2 (9mm)209.7064 L15606.27 m21483.879 L2.0728 TonnesMaterial1/2" Gypsum Fibre Gypsum Board3 mil Polyethylene5/8" Fire-Rated Type X Gypsum Board5/8" Gypsum Fibre Gypsum Board5/8" Moisture Resistant Gypsum Board5/8" Regular Gypsum Board6 mil PolyethyleneAluminiumBallast (aggregate stone)Batt. FiberglassCold Rolled SheetCommercial(26 ga.) Steel CladdingConcrete 20 MPa (flyash av)Concrete 30 MPa (flyash av)Concrete BlocksConcrete BrickEPDM membraneFoam PolyisocyanurateGalvanized SheetGalvanized StudsGlazing PanelIsocyanurateJoint CompoundLarge Dimension Softwood Lumber, kiln-driedModified Bitumen membraneMortarNailsPaper TapePolyester feltPolyethylene Filter FabricRebar, Rod, Light SectionsStandard GlazingWater Based Latex PaintWelded Wire Mesh / Ladder WireScrews Nuts & BoltsSmall Dimension Softwood Lumber, kiln-driedSoftwood PlywoodSolvent Based Alkyd Paint McNicholl 17 Because the BoM does not use consistent units it is not immediately obvious which assemblies account for the greatest resource usage. Predictably, materials such as concrete, aggregate, rebar, glazing, and insulation are present in high quantities. Concrete, aggregate, and rebar are used throughout all assemblies in the superstructure such as columns, beams, slabs, floors, and roofs. Concrete is also used extensively for walls throughout the building. Because of the high degree of uncertainty with the concrete modeling as outlined in the assumptions, it seems likely that these numbers may be an overestimate, particularly if the IE is indeed rounding up beam spans in the estimating process. Other than concrete and its associated components, wall materials such as fiberglass insulation, gypsum drywall, and exterior glazing accounts for the other high material use assemblies. Although assumptions were also made here, most assumptions were related to the type of materials; there is little uncertainty in the volumes used. Although fiberglass insulation thickness was estimated in the metal stud walls around window assemblies, the relative area of this is small and therefore any error would have a proportionally small impact. Similarly, with windows there is little relative uncertainty around the window areas when compared to uncertainty around material used as outlined in the window assumptions section of this document. 4.0 Summary Measures From the final BoM compiled through the different assemblies by the IE the software cross-references an extensive database to determine estimations of environmental impacts in eight impact categories, namely: • Global warming potential (MJ) • Acidification potential (kg) • Eutrophication potential (kg CO2 eq / kg) • Ozone depletion potential (moles of H+ eq / kg) • Photochemical smog potential (kg PM2.5 eq / kg) • Human health respiratory effects potential (kg N eq / kg) McNicholl 18 • Weighted raw resource use (kg CFC-11 eq / kg) • Primary energy consumption (kg NOx eq / kg) As described in the goal and scope section of this document, impacts are determined using mid-point impact assessment methodology, meaning that the potential for environmental harm in terms of equivalent standardized units is determined but the final impacts are not (ie. endpoint effects). Determining final impacts is heavily dependent upon context and current software lacks both the complexity and information required to undertake such a model. As specified in the goal and scope, the impact assessment only includes the manufacturing and construction phases of the building’s life cycle. Impact values for both Tower 4 and the extrapolated values representing the entire complex are presented below: McNicholl 19 Table 4 -1 – Marine Drive Summary Measures Impact CategoryUnitsMaterialTransport-ationTotalMaterialTransport-ationTotalOverallPer Sq. FtPrimary Energy Consumption MJ109,000,000.003,430,000.00112,430,000.005,640,000.0018,800,000.0024,440,000.00136,870,000.00924.05Weighted Resource Use kg84,300,000.00104,000.0084,404,000.00259,000.00429,000.00688,000.0085,092,000.00574.48Global Warming Potential (kg CO2 eq / kg)10,700,000.005,950.0010,705,950.00383,000.0035,400.00418,400.0011,124,350.0075.10Acidification Potential (moles of H+ eq / kg)3,700,000.002,030.003,702,030.00177,000.0011,300.00188,300.003,890,330.0026.26HH Respiratory Effects Potential (kg PM2.5 eq / kg)38,100.002.4538,102.45200.0013.60213.6038,316.050.26Eutrophication Potential (kg N eq / kg)284.000.01284.010.000.090.09284.100.00Ozone Depletion Potential (kg CFC-11 eq / kg)0.020.000.020.000.000.000.020.00Smog Potential (kg NOx eq / kg)56,000.0045.8056,045.804,390.00253.004,643.0060,688.800.41Complex TotalManufacturingConstructionTotal Effects (Man. + Constr.)Impact CategoryUnitsMaterialTransport-ationTotalMaterialTransport-ationTotalOverallPer Sq. FtPrimary Energy Consumption MJ530,839,912.5016,704,411.93547,544,324.4327,467,312.9091,557,709.68119,025,022.58666,569,347.01924.05Weighted Resource Use kg410,548,666.28506,489.46411,055,155.731,261,353.552,089,269.013,350,622.57414,405,778.30574.48Global Warming Potential (kg CO2 eq / kg)52,109,973.0628,977.0452,138,950.101,865,244.83172,401.222,037,646.0554,176,596.1575.10Acidification Potential (moles of H+ eq / kg)18,019,336.489,886.2818,029,222.76862,006.1055,032.03917,038.1218,946,260.8926.26HH Respiratory Effects Potential (kg PM2.5 eq / kg)185,550.4611.93185,562.40974.0266.231,040.25186,602.650.26Eutrophication Potential (kg N eq / kg)1,383.110.071,383.180.000.420.431,383.600.00Ozone Depletion Potential (kg CFC-11 eq / kg)0.090.000.090.000.000.000.090.00Smog Potential (kg NOx eq / kg)272,725.09223.05272,948.1421,379.701,232.1322,611.83295,559.980.41ManufacturingConstructionTotal Effects (Man. + Constr.)Impact Summary Table - Tower 4McNicholl 20 4.1 Impact Comparisons Even when presented in graphical format it is difficult to comprehend the true meaning of such abstract numbers. In order to add some perspective, impacts for each category have been graphed with impact values for other residences at UBC. To normalize the data, impacts have been compiled on a per square foot basis and represent both manufacturing and construction stages, the latter of which is mostly transportation. The data table of values used to generate the following graphs can be found in Appendix C. 4.1.1 Primary Energy Consumption Primary energy consumption simply refers to the estimated amount of power consumed. In this case, the energy demand created by Marine Drive is staggering, outstripping all other residences and amounting to nearly double the average. 0.00 100.00 200.00 300.00 400.00 500.00 600.00 700.00 800.00 900.00 1,000.00VanierTotemGageFariviewThunderbirdMarineDriveAverageEnergy (MJ)Primary Energy Consumption Figure 4-1 – Primary Energy Consumption 4.1.2 Weighted Resource Use Again, Marine Drive residence dramatically outstrips the resource demand of other residences, more than doubling the average value. Although some uncertainty related to column and beam modeling may be disproportionately elevating the value for Marine McNicholl 21 Drive’s resource use, the vast difference between this complex and all other residences is too great to be attributed entirely to model error. 0.00 100.00 200.00 300.00 400.00 500.00 600.00VanierTotemGageFariviewThunderbirdMarineDriveAverageWeighted Use (kg)Weighted Resource UseAverageMarineDriveThunderbirdFariviewGageTotemVanier Figure 4-2 – Weighted Resource Use 4.1.3 Global Warming Potential Global warming potential is determined by calculating the equivalent of CO2 released into the atmosphere and is highly influenced by the amount of concrete in a structure. Again, error in concrete volume, likely attributed to column and beam assembly assumptions could be resulting in falsely high values, but the discrepancy between the Marine Drive residence and the other complexes appears to be indicating a trend. McNicholl 22 0.00 10.00 20.00 30.00 40.00 50.00 60.00 70.00 80.00VanierTotemGageFariviewThunderbirdMarineDriveAveragekg / CO2 eq / kgGlobal Warming PotentialAverageMarineDriveThunderbirdFariviewGageTotemVanier Figure 4-3 – Global Warming Potential 4.1.4 Acidification Potential Acidification potential refers to the equivalent estimated amount of H+ released into the environment. This value is also exceptionally high for the Marine Drive residence with more than double the value of the average. 0.00 5.00 10.00 15.00 20.00 25.00 30.00VanierTotemGageFariviewThunderbirdMarineDriveAveragemoles of H+ eq / kgAcidification PotentialAverageMarineDriveThunderbirdFariviewGageTotemVanier Figure 4-4 – Acidification Potential McNicholl 23 4.1.5 HH Respiratory Effects Potential This index measures the potential for human health respiratory effects as quantified by PM2.5 eq kg. Once again, the impact created by the Marine Drive residence is significantly above that of any other residence at UBC. 0.00 0.05 0.10 0.15 0.20 0.25 0.30VanierTotemGageFariviewThunderbirdMarineDriveAveragekg/ PM2.5 eq / kgHH Respiratory Effects PotentialAverageMarineDriveThunderbirdFariviewGageTotemVanier Figure 4-5 – HH Respiratory Effects Potential 4.1.6 Eutrophication Potential Eutrophication potential refers to the likelihood that the release of nitrogen into an aquatic environment will promote plant an algae growth to the point where the nutrients that were previously scarce are consumed so rapidly that other life is “choked out”. In this case, Thunderbird residence exceeds Marine Drive’s potential for impact, which also may suggest that data in other categories might not be unacceptably skewed. McNicholl 24 0.00 0.00 0.00 0.00 0.00 0.00 0.00VanierTotemGageFariviewThunderbirdMarineDriveAveragekg N eq/ kgEutrophication PotentialAverageMarineDriveThunderbirdFariviewGageTotemVanier Figure 4-6 – Eutrophication Potential 4.1.7 Ozone Depletion Potential Although impact values are relatively low in this category, Marine Drive residence appears to be closer to the expected average value. However, it still seems somewhat surprising that the value is above average. With advancements in material technology aimed at reducing ozone depletion (such as reduction of CFC use) it seems logical to assume that ozone depletion potential should be lower than the average especially when compared to older buildings. McNicholl 25 0.00E+00 2.00E-08 4.00E-08 6.00E-08 8.00E-08 1.00E-07 1.20E-07 1.40E-07 1.60E-07VanierTotemGageFariviewThunderbirdMarineDriveAveragekg CFC-11 eq / kgOzone Depletion PotentialAverageMarineDriveThunderbirdFariviewGageTotemVanier Figure 4-7 – Ozone Depletion Potential 4.1.8 Smog Potential The final impact category, smog potential, once again shows Marine Drive as having the most significant potential for impact. Although it is the newest of the residences, it appears to be having the most significant environmental effects. 0.00 0.05 0.10 0.15 0.20 0.25 0.30 0.35 0.40 0.45VanierTotemGageFariviewThunderbirdMarineDriveAveragekg NOx eq / kgSmog PotentialAverageMarineDriveThunderbirdFariviewGageTotemVanier Figure 4-8 – Smog Potential McNicholl 26 4.2 Impacts By Assembly Impacts were also categorized by assembly type, which allows for comparisons between different parts of the building. A summary of the values generated is presented in the table below. These values are the initial outputs and therefore only represent Tower 4. Table 4-2– Impacts by Assembly Type However, all output values for beams and columns appear as negative numbers, which indicates that an error is occurring somewhere in the software. This seems unusual since all other aspects of the model appear to be functioning properly and producing seemingly reasonable impact estimations. Because of this abnormality, comparisons by assembly type were not explored more thoroughly. 4.3 Impact Assessment Uncertainties In addition to uncertainties resulting from the assumptions made while conducting this study, uncertainty is further generated during the stage of impact assessment in a variety of ways. This next section outlines some of the uncertainty generated in the process of determining impacts from values inputted into the IE. Impact assessment software aims to be as comprehensive and sophisticated as possible but is limited by the amount that can be packed into a program and the memory storage capacity of a computer. Impact assessment experiences tension in two opposing directions since it attempts to simultaneously be sophisticated while being accessible to the average person and therefore the average PC. This broader limitation results in three key areas of uncertainty being generated. FoundationsWalls Beams and ColumnsRoofs Floors Extra Basic Mater2036179.9961469052 -584660.71879 9764877141874 298616.04282690477.049783018 -49652.66733548940765958388 412785.343521319.3277084204 -35653.37857140700315231942 84229.25422347296.8655 45763 -15424.86545906098.79824409 56217.91803259177.832554619 -17671.30757699885.57568992 41834.211288840.92663361645.1 -2015.29900833481.95306691.7 1411.584918258571.1423524049 -17648.129896981167552454 41734.44095259952.7473554027 -17634.87137012167589458 41953.78588Material ID Total Primary Energy Consumption MJ 160158708.9Weighted Resource Use kg 84284422.54Global Warming Potential (kg CO2 eq / kg) 24293044.38Acidification Potential (moles of H+ eq / kg) 16664360.46HH Respiratory Effects Potential (kg PM2.5 eq / kg) 12106836.89Smog Potential (kg NOx eq / kg) 12128973.18Eutrophication Potential (kg N eq / kg) 710055.9652Ozone Depletion Potential (kg CFC-11 eq / kg) 12057277McNicholl 27 The first, as touched on previously in this document, is related to spatial linking. Not only does the database of supporting information need to exist, but a program capable of compiling such information through a geographical information system would be required to assess the related impacts of a specific material source located 20km away over a windy mountain road as compared to a similar facility 100km away across rolling plains. While impact estimators such as IE do take location into account, the true modeling potential that could be realized with more advanced software and processing capacity is not achieved. There is also issue of modeling techniques, which are also limited by the processing capacity of the average PC. Ideally, the most advanced modeling techniques would be used for each impact category, but the depth of each technique varies depending on the history of research in each respective field. One example of advanced modeling that the average computer may not be capable of is related to toxicology. While it may be relatively easy to quantify toxicity released from a given process, further translating that into health impacts and contamination potential is dependent upon determining the probability of toxicity migration through available pathways. This step, from outputs to impacts, is much more difficult to make and consequently outputs are commonly deemed sufficient impact estimation results. However, this means that, even though quantities of a contaminant released may be known, there remains a great deal of uncertainty as to how this will impact either human or environmental health without pathway modeling. The final limitation of software is related to actually modeling uncertainty itself using such techniques as the Monte Carlo simulation. As has been pointed out previously, certain aspects of an LCA make even uncertainty difficult to quantify, but in order to maintain transparency, both uncertainty and a sensitivity analysis should be modeled. If two products were being compared for environmental impact and ranked similarly but the uncertainty of each study could be modeled with reasonable accuracy, this would provide valuable insights for decision makers choosing between the two. However, due to both available data and PC processing capacity, advanced modeling techniques in this field are not currently feasible. McNicholl 28 It should also be noted that the background research in each impact category is not consistent across all fields. Certain areas such as toxicology have much more supporting research than resource usage, which is still emerging. Because of this, it should be recognized that the modeling that impact assessment software uses could be based on new or uncertain research that may prove to be flawed in the future as more is learned in that field. For example, current indicators for resource usage may prove to be incorrect in coming years, which would cause impacts estimated from previous LCA’s to be incorrect as well. This type of uncertainty, uncertainty in the very science impact estimation is base on, is difficult to quantify. Typically, uncertainty tends to propagate as impacts become more specific. The terminology used to address this is commonly midpoint versus endpoint selection. For example, ozone depletion potential is relatively easy to quantify provided that data on such chemical omissions is correct. This would be considered a midpoint case with the endpoint being the true impact on human health such as potential for skin cancer. Since the science correlating to the latter point is less certain, most impact estimators assess impacts based on midpoint criteria. The true effects on human or environmental health remain somewhat uncertain. Finally, the weighting of different impact categories will have an overall effect on the final impact assigned during an assessment. After data is normalized and characterized it is typically grouped into high, medium, and low impact categories and then sometimes aggregated in order to produce a single impact index value. Either a panel of experts of through stakeholder input typically determines weighting of priorities. Regardless, of the method, a high degree of subjectivity is involved at this stage and if the incorrect impact categories are selected as low impact the true validity of the entire study may be thrown into question. Uncertainty could be reduced if anthropocentric prioritization was omitted but, since use of the study will likely rest upon decision makers at some point, this omission may achieve little in the overall reduction of uncertainty. McNicholl 29 5.0 Sensitivity Analysis A sensitivity analysis was conducted on five of the most commonly used materials in the structure in order to estimate the overall sensitivity of the model to errors from assumptions. Conversely, sensitivity can be used to optimize design in order to minimize environmental impacts most effectively. A sensitivity analysis can clearly indicate how significantly different assemblies affect different impacts. For example, if it is found that ozone depletion potential is very sensitive to the use of polyisocyanurate insulation, this may guide a decision to use less of this kind of insulation, resulting in a significant decrease in ozone depletion potential. To conduct the sensitivity analysis 10% material was added as extra basic material and impact summary measures were generated using the IE in separate models. Changes were then plotted as percent differences to show sensitivity. The x-axis represents the percent change in material and the y-values represent the corresponding percent change in impact values for each impact category. The most sensitive impacts can be identified as the ones having the steepest slopes. Table 5-1 – Materials Added for Sensitivity Analysis Material Quantity Addition (+10%) Units 5/8" Fire-Rated Type X Gypsum Board 22304.1 2230.41 m2 Batt. Fiberglass 46579.1 4657.91 m2 (25mm) Concrete 30 MPa (flyash av) 3354664 335466.4 m3 Rebar, Rod, Light Sections 1152869 115287 tonnes Standard Glazing 15606.3 1560.63 m2 5.1 Gypsum Board Sensitivity Using the method described above, gypsum sensitivity was analyzed, yielding the following results. McNicholl 30 Table 5-2 – Gypsum Board Sensitivity Results Gypsum Board Sensitivity-0.40-0.30-0.20-0.100.000.100.200.300.40-15.00 -10.00 -5.00 0.00 5.00 10.00 15.00% Change in MaterialsPrimary Energy Consumption Weighted Resource Use Global Warming PotentialAcidification Potential HH Respiratory Effects Potential Eutrophication Potential Ozone Depletion Potential Smog Potential Figure 5-1 - Gypsum Board Sensitivity The results are both interesting and unexpected since the magnitude of impacts should only increase as the amount of materials used increases. However, it should be recognized that the percent changes in impacts are very small – all less than 1%. Therefore it can likely be concluded that impacts are not very sensitive to the amount of gypsum used and the negative slopes are possibly the result of internal rounding errors within the IE software. 5.2 Fiberglass Sensitivity The following results were found after running a sensitivity analysis on the material. Impact Category Units Initial + 10% Material % DifferencePrimary Energy Consumption MJ 142,760,000.00 142,300,000.00 -0.32Weighted Resource Use kg 88,460,000.00 88,553,000.00 0.11Global Warming Potential (kg CO2 eq / kg) 11,535,160.00 11,529,000.00 -0.05Acidification Potential (moles of H+ eq / kg) 4,004,100.00 4,012,000.00 0.20HH Respiratory Effects Potential (kg PM2.5 eq / kg) 39,120.14 39,218.00 0.25Eutrophication Potential (kg N eq / kg) 295.12 295.10 -0.01Ozone Depletion Potential (kg CFC-11 eq / kg) 0.02 0.02 0.00Smog Potential (kg NOx eq / kg) 62,476.40 62,530.00 0.09Overall ImpactsMcNicholl 31 Table 5-3 – Fiberglass Sensitivity Results Batt Fiberglass Sensitivity-100,000.00-80,000.00-60,000.00-40,000.00-20,000.000.0020,000.0040,000.0060,000.0080,000.00100,000.00-15.00 -10.00 -5.00 0.00 5.00 10.00 15.00% Change in MaterialsPrimary Energy Consumption Weighted Resource Use Global Warming PotentialAcidification Potential HH Respiratory Effects Potential Eutrophication Potential Ozone Depletion Potential Smog Potential Figure 5-2 - Batt Fiberglass Sensitivity All impacts appear to be fairly unaffected by changes in batt fiberglass insulation volumes with the exception of ozone depletion potential. At an incredible change in impact magnitude of almost 90,000 %, the value seems erroneous. However, the input was checked repeatedly; if an error is occurring it is within the IE estimator in the category. In the event that this output is in fact correct then it is clear that the volume of fiberglass batt insulation in a structure dramatically affects the ozone depletion potential, perhaps more so than any other material. Changes in other impacts appear to be almost negligible in comparison. Impact Category Units Initial + 10% Material % DifferencePrimary Energy Consumption MJ 142,760,000.00 142,300,000.00 -0.32Weighted Resource Use kg 88,460,000.00 88,553,000.00 0.11Global Warming Potential (kg CO2 eq / kg) 11,535,160.00 11,529,000.00 -0.05Acidification Potential (moles of H+ eq / kg) 4,004,100.00 4,012,000.00 0.20HH Respiratory Effects Potential (kg PM2.5 eq / kg) 39,120.14 39,218.00 0.25Eutrophication Potential (kg N eq / kg) 295.12 304.00 3.01Ozone Depletion Potential (kg CFC-11 eq / kg) 0.02 16.90 89,308.85Smog Potential (kg NOx eq / kg) 62,476.40 62,530.00 0.09Overall ImpactsMcNicholl 32 5.3 Concrete Sensitivity Concrete sensitivity was analyzed and found to yield the following results. Table 5-4– Concrete Sensitivity Results Concrete Sensitivity-1,500.00-1,000.00-500.000.00500.001,000.001,500.00-15.00 -10.00 -5.00 0.00 5.00 10.00 15.00% Concrete AdditionPrimary Energy Consumption Weighted Resource Use Global Warming PotentialAcidification Potential HH Respiratory Effects Potential Eutrophication PotentialOzone Depletion Potential Smog Potential Figure 5-3 - Concrete Sensitivity From the above graph and table values, it is clear that concrete has a significant impact on all impacts; a rather small difference in concrete added results in higher all around impacts. This suggests that potentially invalid assumptions made as a result of the rigidity of the input fields for assemblies such as concrete beams and columns could be a serious challenge in accurately assessing a building’s impacts. Conversely, this data highlights how smart design resulting in either reduced concrete volumes or more environmentally forms of concrete can significantly reduce the environmental impacts associated with a project. Impact Category Units Initial + 10% Material % DifferencePrimary Energy Consumption MJ 142,760,000.00 778,800,000.00 445.53Weighted Resource Use kg 88,460,000.00 1,031,810,000.00 1,066.41Global Warming Potential (kg CO2 eq / kg) 11,535,160.00 106,519,000.00 823.43Acidification Potential (moles of H+ eq / kg) 4,004,100.00 36,420,000.00 809.57HH Respiratory Effects Potential (kg PM2.5 eq / kg) 39,120.14 262,252.00 570.38Eutrophication Potential (kg N eq / kg) 295.12 345.32 17.01Ozone Depletion Potential (kg CFC-11 eq / kg) 0.02 0.22 1,058.64Smog Potential (kg NOx eq / kg) 62,476.40 555,360.00 788.91Overall ImpactsMcNicholl 33 5.4Rebar, Rod, and Light Sections Sensitivity An analysis of the sensitivity of rebar, rod, and light sections yielded the following results. Table 5-5 – Rebar, Rod, and Light Sections Sensitivity Results Rebar, Rod, Light Sections Sensitivity-8,000.00-6,000.00-4,000.00-2,000.000.002,000.004,000.006,000.008,000.00-15.00 -10.00 -5.00 0.00 5.00 10.00 15.00% Change in MaterialsPrimary Energy Consumption Weighted Resource Use Global Warming PotentialAcidification Potential HH Respiratory Effects Potential Eutrophication Potential Ozone Depletion Potential Smog Potential Figure 5-4 – Rebar, Rod, and Light Sections Sensitivity Although eutrophication potential clearly stands out as an impact highly sensitive to changes in rebar, rod, and light section material volumes, the magnitude of other changes should also be noted. For example, the change in global warming potential, 595%, is nothing to be overlooked. There is also the unusual negative slope of change in smog potential, which seems highly counterintuitive and may suggest that certain bugs embedded in the program are affecting output values. It appears that reductions in rebar, rod, and light section usage in buildings also have high potential for reducing overall building impacts. Impact Category Units Initial + 10% Material % DifferencePrimary Energy Consumption MJ 142,760,000.00 2,373,000,000.00 1,562.23Weighted Resource Use kg 88,460,000.00 296,290,000.00 234.94Global Warming Potential (kg CO2 eq / kg) 11,535,160.00 80,207,000.00 595.33Acidification Potential (moles of H+ eq / kg) 4,004,100.00 5,151,000.00 28.64HH Respiratory Effects Potential (kg PM2.5 eq / kg) 39,120.14 127,324.00 225.47Eutrophication Potential (kg N eq / kg) 295.12 20,600.78 6,880.58Ozone Depletion Potential (kg CFC-11 eq / kg) 0.02 0.02 0.59Smog Potential (kg NOx eq / kg) 62,476.40 10,490.00 -83.21Overall ImpactsMcNicholl 34 5.5 Glazing Sensitivity The final assembly analyzed for sensitivity was glazing, yielding the following results. Table 5-6 - Glazing Sensitivity Results Glazing Sensitivity-2.00-1.50-1.00-0.500.000.501.001.502.00-15 -10 -5 0 5 10 15% Change in MaterialsPrimary Energy Consumption Weighted Resource Use Global Warming PotentialAcidification Potential HH Respiratory Effects Potential Eutrophication Potential Ozone Depletion Potential Smog Potential Figure 5-5 – Glazing Sensitivity Similarly to the gypsum board sensitivity analysis, glazing sensitivity shows a range of different slopes that are all relatively minor (mostly with changes less than 1%) but some of these are negative. Once again, it is uncertain whether or not this is due to internal rounding within the IE impact generation calculations or if there may be a bug within the software somewhere. Interestingly, changes in window surface area appear to do little to affect the overall impact of a building. However, it should be noted that the impacts generated are only analyzing the manufacturing and construction phases of life cycles and windows will have a much larger effect on building energy consumption during the operating phase of Impact Category Units Initial + 10% Material % DifferencePrimary Energy Consumption MJ 142,760,000.00 142,300,000.00 -0.32Weighted Resource Use kg 88,460,000.00 88,553,000.00 0.11Global Warming Potential (kg CO2 eq / kg) 11,535,160.00 11,529,000.00 -0.05Acidification Potential (moles of H+ eq / kg) 4,004,100.00 4,032,000.00 0.70HH Respiratory Effects Potential (kg PM2.5 eq / kg) 39,120.14 39,718.00 1.53Eutrophication Potential (kg N eq / kg) 295.12 295.10 -0.01Ozone Depletion Potential (kg CFC-11 eq / kg) 0.02 0.02 0.00Smog Potential (kg NOx eq / kg) 62,476.40 62,730.00 0.41Overall ImpactsMcNicholl 35 a building’s life as a result of heat loss. The next section of this report will explore building performance as related to heat loss through exterior surfaces and their materials. 6.0 Building Performance The LCA for Marine Drive Residence does not account for operating life or end of life disposal. However, energy usage during operation is still significant and has not been overlooked. The average estimated energy consumption for Tower 1, which is quite similar to Tower 4, is shown here. Average Energy Consumption0100,000200,000300,000400,000500,000600,000700,000October-08 December-08February-09March-09 May-09 July-09 August-09 October-09 December-09January-10MonthkWh Figure 6-1 – Average Energy Consumption Building performance for the operating life of Tower 4 is modeled using a heat loss equation and the areas and types of building envelope materials. Because accurate exterior envelope information was only available for Tower 4, results here are not extrapolated to include the entire complex. In this model, the existing building is compared with another “idealized” building with a few material upgrades that reduce the rate of building heat loss. The idealized building has all of the same material volumes and areas; only the kind of material has been McNicholl 36 substituted. The two buildings are compared to determine energy savings and the energy payback period of installing upgraded materials. Heat loss is calculated using the following equation: Q = (1/R) x A x ∆T Where: R = Calculated R-Value in ft2 ºF h/BTU (Imperial units) A = Assembly of interest ft2 ∆T = Inside Temperature – Outside Temperature in º The following table outlines the R-values used calculating heat losses in both the old and improved buildings: Table 6-6 – Material R-Values Material R-Values 3" Fiberglass Batt Insulation 9.42 4" Polyisocyanurate Insulation 21.6 Low E silver argon filled glazing (3mm glass with 1/2" airspace) 3.75 Standard glazing (double panes, 1/2” airspace) 2.04 Using values from the table above, the exterior envelope of Tower 4 can be summarized as follows. Table 7 - Exterior Assembly Areas Area (ft2) R-value South Windows 6131 2.04 North Windows 6414 2.04 East Windows 10673 2.04 West Windows 11171 2.04 TOTAL 34389 North Walls 6694 9.42 South Walls 7378 9.42 East Walls 7815 9.42 West Walls 7432 9.42 TOTAL 29319 Roof 1 2278 28.8 Roof 3 2026 28.8 Roof 4 7376 28.8 TOTAL 11680 McNicholl 37 Two changes have been made to the existing structure to create the ‘Improved’ building, which was then modeled to determine both embedded energy in material production and heat losses over time. All heating values and surface areas were kept the same but two materials were substituted: • 3” polyisocyanurate insulation was substituted for fiberglass batt insulation in all exterior walls • all exterior windows with standard glazing were substituted with low E silver argon filled glazing The resulting changes in R-values due to these substitutions are summarized in the table below: Table 8 – Current and Improved R-Values R-value: Old Building R-Value New Building Windows 2.04 3.75 Walls 9.42 21.6 Embedded energy was calculated by creating two new IE models that contained only window and insulation assemblies: one for the current building and one for the improved building. The first table shows how the two insulation types were initially compared to ensure that they used the same waste percent additions and therefore could have their volumes interchanged without adjustments having to be made. Table 9 – Insulation Wastes Material input amount output amount waste addition Batt Fiberglass 100 m2 105m2 5% Polyisocyanurate 100 m2 105m2 5% Then, the energy difference between the two sets of basic materials was calculated and added to the embedded energy in the current building to determine the embedded energy in the improved structure. A summary of these values is presented in the table below. Table 10 – Embedded Energy Embedded Energy kWh Joules Current Basic Materials 1370000 4.932E+12 Improved Basic Materials 1550000 5.58E+12 Current Building 8548250 3.07737E+13 Improved Building 8728250 3.14217E+13 McNicholl 38 Energy Usage Over Time05,000,00010,000,00015,000,00020,000,00025,000,00030,000,00035,000,00040,000,00045,000,0000 10 20 30 40 50 60 70 80 90YearsCurrent Building 'Improved Building' Figure 6-2 – Energy Usage Over Time From the graph showing cumulative energy usage over time, it is apparent that the energy payback period is almost instantaneous; net energy begins to be saved immediately. However, although this does appear appealing from an energy perspective, this does not account for other factors such as initial cost and overall environmental impacts. Furthermore, even though it is clear that using better exterior envelope materials can save that energy, it would have to be further investigated to figure out whether it is financially, practically, or environmentally beneficial to replace existing materials with improved ones at this point since construction has already been completed. 7.0 Conclusions There is an appreciable utility in determining average baseline impacts for residences. There is the potential that future decisions on new developments may be able to draw on these results as an environmental reference point. Furthermore, assumptions and McNicholl 39 methodologies documented in this report may be used to provide insight on how future LCAs might be conducted. From impact comparisons, the Marine Drive Residence appears to be responsible for significantly larger environmental impacts than any other residence at UBC. This is surprising since, being the newest residence, one would expect it to be the most environmentally friendly since building policies at UBC continue to shift in that direction. Although uncertainty in the model makes it difficult to draw firm conclusions, it appears that concrete high rises with extensive exterior glazing are the worst option from an environmental perspective, regardless of how modern the technologies or designs incorporated are. McNicholl 40 Appendix A: EIE Input Tables McNicholl 41 All input values are specified for only Tower 4, not the entire complex. Highlighted cells indicate an assumption. General DescriptionProject Location VancouverBuilding Life Expectancy 1 yearBuilding Type ResidentialAssembly Group Assembly Type Input Fields Ideal Inputs Ideal Building Total EIE InputSLABS 8" 10M reinforced slabLength (ft) 103.6 103.6 103.6Width (ft) 103.6 103.6 103.6Thickness (inches) 8 8 8Concrete (psi) 3000 3000 3000Concrete flyash % average average average8" slab on gradeLength (ft) 74.6 74.6 74.6Width (ft) 74.6 74.6 74.6Thickness (inches) 8 8 8Concrete (psi) 3000 3000 3000Concrete flyash % average average average4" Slab on Grade unreinforced*basement level Length (ft) 91.6 91.6 91.6Width (ft) 91.6 91.6 91.6Thickness (inches) 4 4 4Concrete (psi) 3000 3000 3000Concrete flyash % average average averageFOOTINGS Footing F1 Length (ft) 7.5 15 30* 2 per building Width (ft) 7.5 7.5 7.5Thickness (inches) 26 26 13Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #6 #6 #6Footing F2* 6 per building Length (ft) 7.5 45 45Width (ft) 6 6 6Thickness (inches) 18 18 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing F8Length (ft) 5.25 5.25 21Width (ft) 14.5 14.5 14.5Thickness (inches) 48 48 16Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #9, #6, #5 #9, #6, #5 #6Footing F9Length (ft) 5.5 5.5 5.5Width (ft) 3.5 3.5 3.5Thickness (inches) 16 16 16Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing F11Length (ft) 9 9 18Width (ft) 7 7 7Thickness (inches) 30 30 15Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #6 #6 #6Footing F13* 2 per building Length (ft) 8 16 32Width (ft) 8 8 8Thickness (inches) 28 28 14Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #6 #6 #6Footing F14* 2 per building Length (ft) 13 26 78Width (ft) 11 11 11Thickness (inches) 42 42 14Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #7 #7 #6McNicholl 42 McNicholl 43 Footing F15Length (ft) 6.5 6.5 6.5Width (ft) 5.5 5.5 5.5Thickness (inches) 18 18 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing F16Length (ft) 7 7 14Width (ft) 8.5 8.5 8.5Thickness (inches) 30 30 15Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #6 #6 #6Footing F20* 9 per building Length (ft) 5.5 49.5 49.5Width (ft) 4.5 4.5 4.5Thickness (inches) 16 16 16Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing F21Length (ft) 6.5 6.5 6.5Width (ft) 4.5 4.5 4.5Thickness (inches) 12 12 12Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing F22* 5 per building Length (ft) 9 45 45Width (ft) 4.25 4.25 4.25Thickness (inches) 18 18 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing F23* 4 per building Length (ft) 7.5 30 60Width (ft) 7.5 7.5 7.5Thickness (inches) 30 30 15Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #7 #7 #6Footing F24Length (ft) 15 15 30Width (ft) 10 10 10Thickness (inches) 36 36 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #7 #7 #6Footing F25Length (ft) 8.5 8.5 17Width (ft) 8 8 8Thickness (inches) 30 30 15Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #6 #6 #6Footing SF1* 11 per building Length (ft) 9 99 99Width (ft) 1.5 1.5 1.5Thickness (inches) 10 10 10Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing SF2* 7 per building Length (ft) 8 56 56Width (ft) 3.5 3.5 3.5Thickness (inches) 12 12 12Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing SF3* 5 per building Length (ft) 7 35 35Width (ft) 5.25 5.25 5.25Thickness (inches) 18 18 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5McNicholl 44 Footing SF4Length (ft) 15 15 15Width (ft) 2.5 2.5 2.5Thickness (inches) 10 10 10Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #5Footing SF5* 3 per building Length (ft) 19 57 114Width (ft) 9 9 9Thickness (inches) 36 36 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #7 #7 #6Footing SF6* 3 per building Length (ft) 24 72 72Width (ft) 4 4 4Thickness (inches) 18 18 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #6 #6 #6Core FootingLength (ft) 44 44 176*assumed to only exist in the tower structuresWidth (ft) 44 44 44(3 in total complex) Thickness (inches) 60 60 15Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #5 #5 #518" footing w/ 20M* 2 per building Length (ft) 24 48 48Width (ft) 4 8 8Thickness (inches) 18 18 18Concrete (psi) 5333 5333 4000Concrete flyash % average average averageRebar #6 #6 #6STAIRS StairsLength (ft) 14 69.0 69Width (ft) 4 19.7 19.7Thickness (inches) 8 8 8Concrete (psi) 3500 3500 4000Concrete flyash % average average averageRebar #5 #5 #5Stairs Floors 3-5Length (ft) 14 117.6 117.6Width (ft) 4 11.2 11.2Thickness (inches) 8 8 8Concrete (psi) 3500 3500 4000Concrete flyash % average average averageRebar #5 #5 #5Stairs floors 8-17Length (ft) 14 24.4 244Width (ft) 4 7.0 7Thickness (inches) 8 8 8Concrete (psi) 3500 3500 4000Concrete flyash % average average averageRebar #5 #5 #5Stairs 18+Length (ft) 14 33.9 33.9Width (ft) 4 9.7 9.7Thickness (inches) 8 8 8Concrete (psi) 3500 3500 4000Concrete flyash % average average averageRebar #5 #5 #5McNicholl 45 General DescriptionProject Location Vancouver Complex MultiplierBuilding Life Expectancy 1 year Complex MultiplierBuilding Type ResidentialAssembly Group Assembly Type Input Fields Ideal Inputs Building Total EIE InputWALLS concrete walls floors 8-17 Concrete Cast In Place Length (ft) 224 2240 2240Height (ft) 9 9 9Thickness (inches) 8 8 8Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5concrete walls 18+Length (ft) 596 596 596Height (ft) 9 9 9Thickness (inches) 8 8 8Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5thick wallLength (ft) 363 363 363Height (ft) 9 9 9Thickness (inches) 16 16 12Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5Door Type - - Steel Interior DoorNumber of Doors 25 25 25thick walls floors 3-5Length (ft) 94 282 282Height (ft) 9 9 9Thickness (inches) 16 16 12Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5Door Type - - Steel Interior DoorNumber of Doors 8 24 24thick walls floors 8-17Length (ft) 97 970 970Height (ft) 9 9 9Thickness (inches) 16 16 12Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5Door Type - - Steel Interior DoorNumber of Doors 5 50 50thick walls 18+Length (ft) 139 139 139Height (ft) 9 9 9Thickness (inches) 16 16 12Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5Door Type - - Steel Interior DoorNumber of Doors 4 4 4Concrete Wall floors 3-5Length (ft) 459 1377 1377Height (ft) 9 9 9Thickness (inches) 8 8 8Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5Concrete WallLength (ft) 2580 2580 2580Height (ft) 9 9 9Thickness (inches) 8 8 8Concrete (Mpa) 4000 4000 4000Concrete Flyash % average average averageReinforcement #5 #5 #5Concrete block wallEnvelope Concrete Brick CladdingConcrete Brick CladdingConcrete Brick CladdingLength (ft) 1269 1269 1269Height (ft) 9 9 9Rebar (m) #7 #7 #5McNicholl 46 Steel Stud Metal Stud WallWall Type Exterior Exterior ExteriorLength (ft) 1027 1027 1027Height (ft) 9 9 9Door Type wooden door wooden door wooden doorNumber of Doors 6 6 38Total opening area (ft 2) 6688 6688 42335.0Number of window units 716 716 4532Frame Type - - Aluminum FrameGlazing Type - - Standard GlazingSheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing 16 o.c. 16 o.c. 16 o.c.Stud weight - - Light (25 Ga) Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) 3 3 3Metal Stud wall 3-5Wall Type Exterior Exterior ExteriorLength (ft) 379 1137 1137Height (ft) 9 9 9Total opening area (ft 2) 2888 8664 8664Number of window units 288 864 864Frame Type - - Aluminum FrameGlazing Type - - Standard GlazingSheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing 16 o.c. 16 o.c. 16 o.c.Stud weight - - Light (25 Ga) Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) 3 3 3Metal Stud Wall 8- 17Wall Type Exterior Exterior ExteriorLength (ft) 226 2260 2260Height (ft) 9 9 9Total opening area (ft 2) 1641 16410 16410Number of window units 168 1680 1680Frame Type - - Aluminum FrameGlazing Type - - Standard GlazingSheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing 16 o.c. 16 o.c. 16 o.c.Stud weight - - Light (25 Ga) Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) 3 3 3Metal Stud Wall lv 18Wall Type Exterior Exterior ExteriorLength (ft) 238 238 238Height (ft) 9 9 9Total opening area (ft 2) 1503 1503 4509Frame Type - - Aluminum FrameGlazing Type - - Standard GlazingNumber of window units 174 174 174Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing 16 o.c. 16 o.c. 16 o.c.Stud weight - - Light (25 Ga) Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) 3 3 3Metal Stud - interior Drywall PartitionWall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 2832 2832 2832Height (ft) 9 9 9Door Type Hollow Core Wood InteriorHollow Core Wood InteriorHollow Core Wood InteriorNumber of Doors 165 165 165Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) 3 3 3McNicholl 47 Drywall Partition 3-5Wall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 1143 3429 3429Height (ft) 9 9 9Door Type Hollow Core Wood Interior Hollow Core Wood Interior Hollow Core Wood InteriorNumber of Doors 69 207 207Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) 3 3 3Drywall Partition 8-17 Wall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 556 1668 1668Height (ft) 9 9 9Door Type Hollow Core Wood Interior Hollow Core Wood Interior Hollow Core Wood InteriorNumber of Doors 36 108 108Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) 3 3 3Drywal partition lv 18Wall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 304 304 304Height (ft) 9 9 9Door Type Hollow Core Wood Interior Hollow Core Wood Interior Hollow Core Wood InteriorNumber of Doors 30 30 30Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation InsulationMaterial - - fiberglassType batt batt battThickness (inches) - - 3Double Stud DrywallWall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 2220 2220 2220Height (ft) 9 9 9Door Type Hollow Core Wood Interior Hollow Core Wood Interior Hollow Core Wood InteriorStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation InsulationMaterial - - fiberglassType batt batt battThickness (inches) - - 3Double Stud Drywall 3-5Wall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 918 2754 2754Height (ft) 9 9 9Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation insulationMaterial - - fiberglassType batt battThickness (inches) - - 3Double Stud Drywall 8-17Wall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 456 4560 4560Height (ft) 9 9 9Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) - - 3Double Stud Drywall lvl 18Wall Type interior - steel stud interior - steel stud interior - steel studLength (ft) 366 366 366Height (ft) 9 9 9Sheathing type none none noneStud thickness 1 5/8 x 3 5/8 1 5/8 x 3 5/8 1 5/8 x 3 5/8Stud spacing - - 24 o.c.Stud weight - - Light (25 Ga)Category Gypsum Board Gypsum Board Gypsum BoardMaterial Gypsum Type X 5/8" Gypsum Type X 5/8" Gypsum Type X 5/8"Category Insulation Insulation insulationMaterial - - fiberglassType batt batt battThickness (inches) - - 3Curtain Wall Ground Floor Curtain WallWall Type Exterior Exterior ExteriorLength (ft) 125 125 125Height (ft) 14.91 14.91 14.91Total opening area (ft 2 ) 6405 6405 6405Number of window units 138 138 138Number of Doors 3 3 3Door Type wooden door wooden door wooden doorPanel Type metal spandrel panel metal spandrel panel metal spandrel panelPercent Viewable Glazing 71.5 71.5 71.5Percent Spandrel Panel 28.5 28.5 28.5Thickness of Insulation (inches) - - 3McNicholl 48 Assembly Group Assembly Type Input Fields Ideal Inputs Ideal Building Total EIE Input1FLOORS Concrete Suspended Slab Floor2 TotalFloor width (ft) 64 64 272.43Span (ft) 127.7 127.7 30Live load (kips) 2 2 100 psfType Floor Floor FloorConcrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope none none noneConcrete Suspended Slab Floor3-5 Floor width (ft) 78.6 235.8 235.8Span (ft) 157.2 471.6 471.6Live load (kips) 2 2 100 psfType Floor Floor FloorConcrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope none none noneConcrete Suspended Slab Floor6 & 7 TotalFloor width (ft) 88 88 88Span (ft) 176 176 176Live load (kips) 2 2 100 psfType Floor Floor FloorConcrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope none none noneConcrete Suspended Slab Floor 8-17 Floor width (ft) 55.5 555 555Span (ft) 111 1110 1110Live load (kips) 2 2 100 psfType Floor Floor FloorConcrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope none none noneConcrete Suspended Slab Floor18+Floor width (ft) 72.8 72.8 72.8Span (ft) 145.5 145.5 145.5Live load (kips) 2 2 100 psfType Floor Floor FloorConcrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope none none noneROOFING R4 Type Roofing Roofing Type Concrete Suspended SlabConcrete Suspended SlabConcrete Suspended SlabFloor width (ft) 85.9 85.9 85.9Span (ft) 85.9 85.9 85.9Live load (kips) 0.3 0.3 0.3Concrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope Roof envelope Roof envelope Roof envelopeMaterial Ballast (aggregate stones)Ballast (aggregate stones)Ballast (aggregate stones)Envelope EPDM Inverted EPDM Inverted EPDM InvertedMaterial Polyisocyanurate Polyisocyanurate PolyisocyanurateThickness 4" 4" 4"R3 Type RoofingRoofing Type Concrete Suspended SlabConcrete Suspended SlabConcrete Suspended SlabFloor width (ft) 21 31.82 31.82Span (ft) 48.2 63.63 63.63Live load (kips) 0.3 0.3 0.3Concrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope Vapour Barrier Vapour Barrier Vapour BarrierMaterial - - 3mil PolyEnvelope EDPM Membrane EDPM Membrane EDPM MembraneMaterial Polyisocyanurate Polyisocyanurate PolyisocyanurateThickness 4" 4" 4"R1 Type Roofing Roofing Type Concrete Suspended SlabConcrete Suspended SlabConcrete Suspended SlabFloor width (ft) 33.7 33.7 33.7Span (ft) 67.5 67.5 67.5Live load (kips) 0.3 0.3 0.3Concrete (psi) 3500 3500 4000Concrete Flyash % Average Average AverageEnvelope Vapour Barrier Vapour Barrier Vapour BarrierMaterial - - 3mil PolyEnvelope Insulation Insulation InsulationMaterial Polyisocyanurate Polyisocyanurate PolyisocyanurateThickness 4" 4" 4"Envelope Steel Roof System Steel Roof System Steel Roof SystemMaterial - - CommercialTrellis SoffitRoof Width (ft) 10 10 10Roof Length (ft) 74 74 74Decking none none noneLive load (psf) - - 45McNicholl 49 Assembly Group Assembly Type Input Fields Ideal Inputs Building Total EIE InputCOLUMNS Ground Floor South PodiumConcrete Beams and Columns Number of columns 9 9 9Number of beams 8 8 8Floor to floor height (ft) 9 9 9Bay sizes (ft) 10.97 10.97 10.97Supported span 4.87 4.87 4.87Live load (kips) 2 2 100 psfGround Floor Tower CenterNumber of columns 14 14 14Number of beams 11 11 11Floor to floor height (ft) 9 9 9Bay sizes (ft) 10 10 10Supported span 3.91 3.91 3.91Live load (kips) 2 2 100 psfGround Floor North PodiumNumber of columns 7 7 7Number of beams 8 8 8Floor to floor height (ft) 9 9 9Bay sizes (ft) 10 10 10Supported span 5.21 5.21 5.21Live load (kips) 2 2 100 psfFloor 2 South PodiumNumber of columns 9 9 9Number of beams 5 5 5Floor to floor height (ft) 9 9 9Bay sizes (ft) 10 10 10Supported span 4.43 4.43 4.43Live load (kips) 2 2 100 psfFloor 2 Tower CenterNumber of columns 7 7 7Number of beams 5 5 5Floor to floor height (ft) 9 9 9Bay sizes (ft) 20.94 20.94 20.94Supported span 7.48 7.48 7.48Live load (kips) 2 2 100 psfFloor 2 North PodiumNumber of columns 10 10 10Number of beams 9 9 9Floor to floor height (ft) 9 9 9Bay sizes (ft) 10 10 10Supported span 4.11 4.11 4.11Live load (kips) 2 2 100 psfFloors 3-5 South PodiumNumber of columns 9 27 27Number of beams 7 21 21Floor to floor height (ft) 9 9 9Bay sizes (ft) 11.39 11.39 11.39Supported span 4.43 4.43 4.43Live load (kips) 2 2 100 psfFloors 3-5 Tower CenterNumber of columns 17 51 51Number of beams 11 33 33Floor to floor height (ft) 9 9 9Bay sizes (ft) 10.84 10.84 10.84Supported span 3.51 3.51 3.51Live load (kips) 2 2 100 psfFloors 3-5 North PodiumNumber of columns 6 18 18Number of beams 6 18 18Floor to floor height (ft) 9 9 9Bay sizes (ft) 12.11 12.11 12.11Supported span 6.05 6.05 6.05Live load (kips) 2 2 100 psfFloor 6 South PodiumNumber of columns 13 13 13Number of beams 5 5 5Floor to floor height (ft) 9 9 9Bay sizes (ft) 11.46 11.46 11.46Supported span 4.46 4.46 4.46Live load (kips) 2 2 100 psfMcNicholl 50 Floor 6 Tower CenterNumber of columns 15 15 15Number of beams 9 9 9Floor to floor height (ft) 9 9 9Bay sizes (ft) 12.69 12.69 12.69Supported span 3.81 3.81 3.81Live load (kips) 2 2 100 psfFloor 6 North PodiumNumber of columns 5 5 5Number of beams 7 7 7Floor to floor height (ft) 9 9 9Bay sizes (ft) 10 10 10Supported span 6.63 6.63 6.63Live load (kips) 2 2 100 psfFloors 7 South PodiumNumber of columns 10 9 9Number of beams 10 8 8Floor to floor height (ft) 9 9 9Bay sizes (ft) 11.63 10.97 10.97Supported span 3.5 4.87 4.87Live load (kips) 2 2 100 psfFloors 7 Tower CenterNumber of columns 17 9 57Number of beams 6 5 32Floor to floor height (ft) 9 9 9Bay sizes (ft) 19.2 17 17Supported span 3.39 18 18Live load (kips) 2 2 100 psfFloors 8-17 Tower CenterNumber of columns 17 170 170Number of beams 9 90 90Floor to floor height (ft) 9 9 9Bay sizes (ft) 12.84 12.84 12.84Supported span 3.4 3.4 3.4Live load (kips) 2 2 100 psfFloor 18 Tower CenterNumber of columns 16 9 57Number of beams 8 5 32Floor to floor height (ft) 9 9 9Bay sizes (ft) 14.06 17 17Supported span 3.52 18 18Live load (kips) 2 2 100 psfAssembly Group Assembly Type Input Fields Ideal Inputs Building Total EIE Input1EXTRA BASIC MATERIALS 5c Gypsum Board1/2" regular gypsum board (ft2) 570 570 5704000 psi Average Flyash Concrete (yrd 3) 194.89 194.89 194.89McNicholl 51 Appendix B: Detailed Assumptions McNicholl 52 Assembly Group Assembly Type Assembly Name Specific AssumptionsCOLUMNSConcrete Beams and Columns Ground Floor South PodiumGround Floor Tower CenterGround Floor North PodiumFloor 2 South PodiumFloor 2 Tower CenterFloor 2 North PodiumFloor 3-5 South PodiumThe number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(5484/2) / 7 = 7.48 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(5484/2) / 5 = 20.94 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(3376/2) / 10 = 4.11 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(3376/2) / 9 = 10 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(3179/2) / 9 = 4.43 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(3179/2) / 7 = 11.39 ft Since this represents one of three identical floors, the number of beams and columns were each multiplied by three to get the final input. Due to the rigidity of the impact modeling software and the non-uniformity of the column assembly within the tower, modeling this part of the structure required the largest assumptions and appears to be the greatest source of error within the model. Athena Impact Estimator models column and beam assemblies in a grid format, which assumes that bay areas and spans are uniform. It also places minimum values on bay areas and span lengths and will round up to these minimums if an input value is outside the range. In order to conform to this input format, the number of columns and beams were counted, the supported area was determined, and then transformed mathematically into a rectangular grid where length = 2 x width. Since no drawings detailing beams were available the location of certain beams had to be assumed; beams were only assumed to exist if the length of a span between two columns exceeded 10 ft. Although all beams and columns counted in the quantity takeoffs are represented in the model, the values for supported spans are below the minimum required input value, which means that the software may be rounding up the lengths of beams even if this is not evident in the input fields. If rounding is occurring, span values will be rounded up to approximately 20 ft. This cannot be changed without reducing the value for bay areas, which would result in a value below the valid input range and cause the model to not function.Also, input fields in Athena do not allow for concrete strengths to be specified, only live loads. This may be missing an important component in environmental impacts since the concrete strengths change from 25 MPa to 35 MPa from the top of the structure to the bottom. Since these strengths have a significant affect on greenhouse gas emissions, the assumption that all column strengths are the same may not be valid.The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(6006/2) / 14 = 3.91 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(6006/2) / 11 = 10 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams, whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(2659/2) / 7 = 5.21 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(2659/2) / 8 = 10 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(3184/2) / 9 = 4.43 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(3184/2) / 5 = 10 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(3847/2) / 9 = 4.87 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(3847/2) / 8 = 10.97 ft McNicholl 53 Floor 3-5 Tower CenterFloor 3-5 North PodiumFloor 6 South PodiumFloor 6 Tower CenterFloor 6 North PodiumFloor 7 South PodiumFloor 7 Tower CenterFloors 8-17 Tower CenterFloor 18 Tower CenterThe number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(3179/2) / 10 = 3.5 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(3179/2) / 10 = 11.63 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(7111/2) / 17 = 3.51 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(7111/2) / 11 = 10.84 ft Since this represents one of three identical floors, the number of beams and columns were each multiplied by three to get the final input. The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(2201/2) / 5 = 6.63 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(2201/2) / 7 = 10 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(6637/2) / 17 = 3.39 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(6637/2) / 6 = 19.2 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(6678/2) / 17 = 3.4 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(6678/2) / 9 = 12.84 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(6327/2) / 16 = 3.52 The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(2638/2) / 6 = 6.05 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(2638/2) / 6 = 12.11 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(3220/2) / 13 = 4.46 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(3220/2) / 5 = 11.46 ft The number of columns and supported areas were determined in onscreen, as well as the number of beams whose positions were approximated. The assembly was modeled as a grid with dimensions calculated in the following way to ensure that values were within acceptable ranges for EIE input software (ie bay size > 10ft). sqrt(area/2) / # of columns = Span sqrt(6525/2) / 15 = 3.81 ft 2 x sqrt(area/2) / # of beams = Bay Size 2 x sqrt(6525/2) / 9 = 12.69 ft McNicholl 54 Assembly Group Assembly Type Assembly Name Specific AssumptionsFLOORSConcrete Suspended Slab Concrete Suspended Slab Floor2 TotalConcrete Suspended Slab Floor3-5 Concrete Suspended Slab Floor6 & 7 TotalConcrete Suspended Slab Floor 8-17 x 10Concrete Suspended Slab Floor18+ROOFINGConcrete Suspended Slab R4 Type Roofing * approximated to be a squareR3 Type Roofing* 2 slabs of thisR1 Type Roofing Trellis Soffit Trellis SoffitIn consistency with other concrete bodies in the structure, since there is no indication of increased fly ash content it was assumed that all concrete contained only average concentrations of flyash. One slight modification was made to the concrete in order to fit EIE input fields: the strength of concrete was adjusted from 3500 to 4000 psi. Although this will likely result in a higher overall global warming potential in the model, the magnitude of this increase is unknown and therefore not adjusted for. Two other general assumptions were also made due to lack of specific information available from the drawings. No floor envelope specifications were provided and since flooring such as carpeting is beyond the scope of this study, floors were assumed to not have envelopes. The other source of uncertainty is related to floor loading specifications, which were indicated in the structural drawings as having a point load of 2 kips. It is unusual to attribute a point load to a floor area, so this was assumed to translate into a uniform area load of 100 psf in order to fit EIE input fields. The slab was area was determined in the takeoffs and then adjusted in size to fit within the parameters of the impact estimation software, which limits the span to no more than 30 ft. Span Length = Area / 30 ft = 8172.9 ft 2 / 30 ft = 272.43 ft The slab was area was determined in the takeoffs and then adjusted in size to fit within the parameters of the impact estimation software, which limits the span to no more than 30 ft. The area modeled in the takeoff software represents one of three identical floors so the area of one floor has been multiplied by 3 to obtain the final area. Area x 3 = Total Area 37067.8 ft 2 x 3 = 111203.4 Span Length = Total Area / 30 ft = 111203.4 ft 2 / 30 ft = 3706.78 ftThe slab was area was determined in the takeoffs and then adjusted in size to fit within the parameters of the impact estimation software, which limits the span to no more than 30 ft. Span Length = Area / 30 ft = 15488.1 ft 2 / 30 ft = 516.27 ftThe slab was area was determined in the takeoffs and then adjusted in size to fit within the parameters of the impact estimation software, which limits the span to no more than 30 ft. The area modeled in the takeoff software represents one of ten identical floors so the area of one floor has been multiplied by 10 to obtain the final area. Area x 10 = Total Area 205350 ft 2 x 10 = 616050 ft 2 Span Length = Total Area / 30 ft = 616050 ft 2 / 30 ft The slab was area was determined in the takeoffs and then adjusted in size to fit within the parameters of the impact estimation software, which limits the span to no more than 30 ft. Span Length = Area / 30 ft = 10592.4 ft 2 / 30 ft = 353.08 ftSimilarly to the floors, no unusual concrete flyash concentrations were specified and loading specifications were also given as point loads, specifically as 0.3 kips. In an attempt to be proportionally consistent with other loading assumptions, 0.3 kips was correlated to 45 psf in the EIE software. Also, roof concrete strengths were specified as 3500 psi in structural drawings but had to be rounded up to 4000 to fit EIE input fields, likely resulting a slightly increased global warming potential for the overall model.Roof schedules are well detailed in architectural drawings. Area determined in takeoff software was approximated as a square for EIE input. Sqrt(area) = length sqrt(7378.8 ft 2 ) = 85.9 ftRoof schedules are well detailed in architectural drawings. The vapour barrier was assumed to be made of 3 mil poly. Area determined in takeoff software was approximated as a rectangle of 2w = l for EIE input. The total area of two identical slabs was found by multiplying the dimensions of one by a factor of 2. area x 2 = total area 1012.2 x2 = 2024.4 ft 2 Sqrt(total area /2 ) = width sqrt(2024.4 ft 2 ) = 31.82 ft l = 2 x w = 63.63 ftRoof schedules are well detailed in architectural drawings. The vapour barrier was assumed to be made of 3 mil poly. Area determined in takeoff software was approximated as a square for EIE input. Sqrt(area) = length sqrt( ft2) = 85.9 ftThe trellis soffit is a decorative structure arching over the tower entrance. It has no decking and carries no load, but a minimum load of 45 psf was specified in order to comply with EIE input fields.McNicholl 55 Assembly Group Assembly Type Assembly Name Specific AssumptionsWALLSconcrete walls floors 8-17 thick wallthick walls floors 3-5* 3 identical floors per buildingthick walls floors 8-17* 10 identical floors per towerthick walls 18+*floor 18 and roofConcrete Wall floors 3-5* 3 identical floors per buildingConcrete block wallThis wall represents one of 10 identical floors. Total wall length was multiplied by 10 to account for all repeated wall units. Length * 10 = Input Length 224 ft * 10 = 2240 ftWall thicknesses are limited to 8" or 12" in the EIE input fields. To account for the extra concrete in this 16" wall, the missing volume was added to extra basic materials. Length * (4/3 ft - 1 ft) * height = volume added 363 ft * 1/3 ft * 9 ft = 1089 ft 3 This wall represents one of 3 identical floors. Total wall length was multiplied by 3 to account for all repeated wall units. Length * 3 = Input Length 224 94ft * 3 = 282 ftWall thicknesses are limited to 8" or 12" in the EIE input fields. To account for the extra concrete in this 16" wall, the missing volume was added to extra basic materials. Length * (4/3 ft - 1 ft) * height = volume added 282 ft * 1/3 ft * 9 ft = 846 ft 3 This wall represents one of 10 identical floors. Total wall length was multiplied by 10 to account for all repeated wall units. Length * 10 = Input Length 97 * 10 = 970 ftWall thicknesses are limited to 8" or 12" in the EIE input fields. To account for the extra concrete in this 16" wall, the missing volume was added to extra basic materials. Length * (4/3 ft - 1 ft) * height = volume added 970 ft * 1/3 ft * 9 ft = 2910 ft 3Wall thicknesses are limited to 8" or 12" in the EIE input fields. To account for the extra concrete in this 16" wall, the missing volume was added to extra basic materials. Length * (4/3 ft - 1 ft) * height = volume added 139 ft * 1/3 ft * 9 ft = 417 ft 3 This wall represents one of 3 identical floors. Total wall length was multiplied by 3 to account for all repeated wall units. Length * 3 = Input Length 459ft * 3 = 1377 ftRebar is specified as #7 in drawings but was rounded down to the maximum input value of #5 in the EIE. Door types specified in the model have been confirmed through drawings and a site visit but the generic terms used in the EIE make it uncertain if doors used in the model are an accurate representation of the actual ones. However, it seems likely that this assumption is a minor one since the type of materials has been confirmed and it is only the volume that remains uncertain.Windows were accounted for by counting the number of each type of assembly and then matching them to the areas specified in the window schedule in the architectural drawings. In cases where the window assembly did not match any detailed in the window schedule, an assumption was made based on size and the number of windows and the new assembly was equated to one specified in the window schedule. A complete breakdown of these assumptions and count for the total number of windows can be referenced later in this Appendix. Two more assumptions related to the window assemblies were made when the architect was unable to verify drawing ambiguities. The windows were assumed to be of standard glazing with aluminum frames.There was also limited information about the envelopes of the metal stud walls immediately surrounding the windows. These envelopes were assumed to be the same as the single stud drywall partition envelopes that the metal stud walls join to except with a commercial grade steel exterior cladding. Also, due to a few missing specifics in the architectural drawings, steel studs in drywall partitions were assumed to be light (25 Ga) and acoustic batt insulation was interpreted as fiberglass. McNicholl 56 Metal Stud Double Stud Drywall* the wall is double thickness (ie 2 studs)modeled by doubling the length of the actual wall*consequently, only one layer of drywall was modeled Double Stud Drywall 3-5*3 identical floors per building* the wall is double thickness (ie 2 studs)modeled by doubling the length of the actual wallDouble Stud Drywall 8-17* 10 identical floors per tower * the wall is double thickness (ie 2 studs)modeled by doubling the length of the actual wallDouble Stud Drywall lvl 18* the wall is double thickness (ie 2 studs)modeled by doubling the length of the actual wall Ground Floor Curtain WallThis wall is twice the thickness of the standard drywall partitions, which has been modeled by doubling the length of the wall determined through takeoffs. Consequently, gypsum board drywall has only been modeled on one side of the wall. Length * 2 = input length 1110 ft * 2 = 2220 ft The thickness of insulation, 3", was assumed to be consistent with that of the single stud drywall partitions. This wall is twice the thickness of the standard drywall partitions, which has been modeled by doubling the length of the wall determined through takeoffs. Consequently, gypsum board drywall has only been modeled on one side of the wall. Length * 2 = input length 459 ft * 2 = 918 ft Since this represents one of three identical floors, this length was multiplied by three to obtain the final input. Input length * 3 = final input 918 ft * 3 = 2754 ft The thickness of insulation, 3", was assumed to be consistent with that of the single stud drywall partitions. This wall is twice the thickness of the standard drywall partitions, which has been modeled by doubling the length of the wall determined through takeoffs. Consequently, gypsum board drywall has only been modeled on one side of the wall. Length * 2 = input length 228 ft * 2 = 456 ft Since this represents one of three identical floors, this length was multiplied by three to obtain the final input. Input length * 3 = final input 456 ft * 10 = 4560 ft The thickness of insulation, 3", was assumed to be consistent with that of the single stud drywall partitions. This wall is twice the thickness of the standard drywall partitions, which has been modeled by doubling the length of the wall determined through takeoffs. Consequently, gypsum board drywall has only been modeled on one side of the wall. Length * 2 = input length 183 ft * 2 = 366 ft Thickness of insulation was assumed to be consistent with that of the single stud drywall partitions. The thickness of insulation was assumed to be consistent with that of the other metal walls surrounding windows: 3"McNicholl 57 Assembly Group Assembly Type Assembly Name Specific AssumptionsSLABS Slab On Grade 8" 10M reinforced slab8" slab on grade4" Slab on Grade unreinforcedFOOTINGS Concrete Footing Footing F1Footing F2Footing F8Footing F11Footing F13Footing F14Footing F16 Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 30 in. / 2 = 15 in. 7 ft *2 = 14 ft This footing has a combination of different rebar sizes that were averaged to #6 size.Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 48 in. / 4 = 16 in. 5.25 ft *4 = 21 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 30 in. / 2 = 15 in. 9 ft *2 = 18 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 28 in. / 2 = 14 in. 8 ft *2 = 16 ft Since there are two identical footings, the length is muliplied by 2 to find the final input length. input length * 2 = final input length 16 ft * 2 = 32 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 42 in. / 3 = 14 in. 13 ft *3 = 39 ft Since there are two identical footings, the length is muliplied by 2 to find the final input length. input length * 2 = final input length 39 ft * 2 = 78 ft Modeled as a square area. Sqrt (area) = length = width sqrt(5565 ft 2) = 74.6 ft Modeled as a square area. Sqrt (area) = length = width sqrt(8391 ft2) = 91.6 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 26 in. / 2 = 13 in. 7.5 ft *2 = 15 ft Since there are two identical footings, the length is muliplied by 2 to find the final input length. input length * 2 = final input length 15 ft * 2 = 30 ft Since there are six identical footings, the length is muliplied by 6 to find the final input length. input length * 6 = final input length 7.5 ft * 6 = 45 ftSince there are no rebar inputs in the modeling software, it was assumed that all concrete slabs on grade contain minimum reinforcement in the form of #10M bars. Modeled as a square area. Sqrt (area) = length = width sqrt(10733 ft 2) = 103.6 ft Concrete flyash content was again assumed to be average and the concrete strength of 5333 psi had to be changed to 4000 psi in order to match available input options for all footings. Again, this rigidity in input format is contributing to inaccuracies in greenhouse gas emissions estimated by the model. In some cases, the size of rebar also had to be changed to match available input fields. There is no input category in the EIE that represents stairs. Stairs were modeled as footings in order to have more control over concrete volumes and reinforcement dimensions in the model.McNicholl 58 Footing F20Footing F22Footing F23Footing F24Footing F25Footing SF1* 11 per buildingFooting SF2* 7 per buildingFooting SF3* 5 per buildingFooting SF5* 3 per buildingFooting SF6* 3 per buildingSince there are nine identical footings, the length is muliplied by 9 to find the final input length. length * 9 = final input length 5.5 ft * 9 = 49.5 ft Since there are five identical footings, the length is muliplied by 5 to find the final input length. length * 5 = final input length 9 ft * 5 = 45 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 30 in. / 2 = 15 in. 7.5 ft *2 = 15 ft Since there are four identical footings, the length is muliplied by 4 to find the final input length. input length * 4 = final input length 15 ft * 4 = 60 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 36 in. / 2 = 18 in. 15 ft *2 = 30 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 30 in. / 2 = 15 in. 8.5 ft *2 = 17 ft Since there are eleven identical footings, the length is muliplied by 11 to find the final input length. length * 11 = final input length 9 ft * 11 = 99 ft Since there are seven identical footings, the length is muliplied by 7 to find the final input length. length * 7 = final input length 8 ft * 7 = 56 ft Since there are five identical footings, the length is muliplied by 5 to find the final input length. length * 5 = final input length 7 ft * 5 = 35 ft Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 36 in. / 2 = 18 in. 19 ft *2 = 38 ft Since there are three identical footings, the length is muliplied by 3 to find the final input length. input length * 3 = final input length 38 ft * 3 = ft Since there are three identical footings, the length is muliplied by 3 to find the final input length. length * 3 = final input length 24 ft * 3 = 72 ft McNicholl 59 Core Footing18" footing w/ 20M* 2 per buildingSTAIRS Concrete Footing StairsStairs Floors 3-5Stairs floors 8-17Stairs 18+Assembly Group Assembly Type Assembly Name Specific AssumptionsBASIC MATERIALS Concrete Cast In Place 4000 psi Average Flyash Concrete (yrdThe total area of stairs was determined and modeled as a single footing for each set. Dimensions were determined as follows using the length to width ratio for a single flight of stairs. Thickness was averaged across the length of the stairs. All other specs are from the structural drawings. sqrt(area *4 / 14) = length length * 4 / 14 = width sqrt (438*4/14) = 39.2 ft ft *4 / 14 = 11.2 ft Since this represents one of three identical floors length is then multiplied by three. Length = 39.2 * 3 = 117.6 ft The total area of stairs was determined and modeled as a single footing for each set. Dimensions were determined as follows using the length to width ratio for a single flight of stairs. Thickness was averaged across the length of the stairs. All other specs are from the structural drawings. sqrt(area *4 / 14) = length length * 4 / 14 = width sqrt (170*4/14) = 24.4 ft ft *4 / 14 = 7 ft Since this represents one of ten identical floors length is then multiplied by 10 Length = 24.4 * 10 = 244 ft The total area of stairs was determined and modeled as a single footing for each set. Dimensions were determined as follows using the length to width ratio for a single flight of stairs. Thickness was averaged across the length of the stairs. All other specs are from the structural drawings. sqrt(area *4 / 14) = length length * 4 / 14 = width sqrt (1361*4/14) = 69 ft 69 ft *4 / 14 = 19.7 ftVolume added is the sum of the volumes remainin from the thick concrete walls: 1089 ft 3 + 846 ft 3 +2910 ft 3 + 417 ft 3 = 5262 ft 3 27 ft 3 = 1 yrd 3 5262 ft 3 /27 ft 3/yrd 3 = 194.89 yrd 3 Limitations on maximum footing thickness forced changes in footing dimensions. The volume of concrete within the footing has been kept constant by increasing footing length and reducing footing thickness simultanously. original thickness / = input thickness original length * = input length 60 in. / 4 = 15 in. 44 ft *4 = 176 ft Since there are two identical footings, the length is muliplied by 2 to find the final input length. length * 2 = final input length 24 ft * 2 = 48 ft The total area of stairs was determined and modeled as a single footing for each set. Dimensions were determined as follows using the length to width ratio for a single flight of stairs. Thickness was averaged across the length of the stairs. All other specs are from the structural drawings. sqrt(area *4 / 14) = length length * 4 / 14 = width sqrt (1361*4/14) = 69 ft 69 ft *4 / 14 = 19.7 ftMcNicholl 60 Window Assumptions and Calculations Window Assemblies # Windows Sub-wins/Wins Total Wins 1 16 2 32 2 42 3 126 3 3 15 45 5 7 9 63 6 14 12 168 6A 3 16 48 7 3 6 18 8 21 6 126 9 3 6 18 4 6 12 72 716 Floors 8-17 6 8 12 96 8 4 6 24 2 16 3 48 168 Floor 18 6 6 12 72 2 2 3 6 9 2 6 12 8 8 6 48 7 6 6 36 174 Floors 3-5 1 12 2 24 2 8 3 24 3 8 15 120 6 4 12 48 7 3 6 18 8 7 6 42 9 2 6 12 288 Window equivalents in window schedule for unspecified window units: 36 = type 6 barb4right 12 windows total 22 = type 2 barb4right 3 windows total 18 = type 8 barb4right 8 windows total 35 = type 6 barb4right 12 windows total 23 = type 2 barb4right 3 windows total McNicholl 61 29 = type 2 barb4right 3 windows total 52 = type 8 barb4right 8 windows total 28 = type 1 barb4right 2 windows total 41 = type 6 barb4right 12 windows total 26 = type 2 barb4right 3 windows total 39 = type 9 barb4right 6 windows total 38 = type 6 barb4right 12 windows total 37 = 3 x type 7 barb4right 6 windows each 19 = type 9 barb4right 6 windows total 20 = type 2 barb4right 3 windows total 45 = type 8 barb4right 8 windows total 46 = type 8 barb4right 8 windows total 48 = type 1 barb4right 2 windows total 21 = type 2 and type 1 barb4right 5 total 32 = type 3 barb4right 15 windows total 43 = type 3 barb4right 15 windows total 33 = type 3 barb4right 15 windows total 23 = type 2 barb4right 3 windows total 25 = type 2 barb4right 3 windows total 28 = type 2 barb4right 3 windows total 31 = type 2 barb4right 3 windows total McNicholl 62 Appendix C: Aggregated Summary Measures for Residences at UBC McNicholl 63 VanierTotemGageFariviewThunderbirdMarineDriveAverageImpact CategoryUnits1959,1961,196819641972198519952005Primary Energy Consumption MJ288.43404.14328.49282.91495.45924.05453.91Weighted Resource Use kg116.42196.50182.1599.98182.69574.48225.37Global Warming Potential (kg CO2 eq / kg)20.1129.5625.6416.7428.4075.1032.59Acidification Potential (moles of H+ eq / kg)3.6610.1310.657.036.1026.2610.64HH Respiratory Effects Potential (kg PM2.5 eq / kg)0.050.080.130.090.070.260.12Eutrophication Potential (kg N eq / kg)0.000.000.000.000.000.000.00Ozone Depletion Potential (kg CFC-11 eq / kg)1.81E-083.27E-084.92E-081.55E-071.58E-071.23E-078.94E-08Smog Potential (kg NOx eq / kg)0.060.140.180.090.100.410.16Residences
- Library Home /
- Search Collections /
- Open Collections /
- Browse Collections /
- UBC Undergraduate Research /
- Building Life Cycle Assessment: Marine Drive Residence...
Open Collections
UBC Undergraduate Research
Building Life Cycle Assessment: Marine Drive Residence at The University of British Columbia McNicholl, Duncan 2009-03-27
pdf
Page Metadata
Item Metadata
Title | Building Life Cycle Assessment: Marine Drive Residence at The University of British Columbia |
Creator |
McNicholl, Duncan |
Contributor | University of British Columbia. Sustainability Office |
Date Issued | 2009-03-27 |
Description | Disclaimer: “UBC SEEDS provides students with the opportunity to share the findings of their studies, as well as their opinions, conclusions and recommendations with the UBC community. The reader should bear in mind that this is a student project/report and is not an official document of UBC. Furthermore readers should bear in mind that these reports may not reflect the current status of activities at UBC. We urge you to contact the research persons mentioned in a report or the SEEDS Coordinator about the current status of the subject matter of a project/report.” |
Type |
Text |
Language | eng |
Collection |
UBC Social Ecological Economic Development Studies (SEEDS) Student Reports |
Series | University of British Columbia. CIVL 498 UBC Social Ecological Economic Development Studies (SEEDS) Student Report |
Date Available | 2010-03-03 |
Provider | Vancouver : University of British Columbia Library |
DOI | 10.14288/1.0077962 |
URI | http://hdl.handle.net/2429/21440 |
Affiliation |
Applied Science, Faculty of Civil Engineering, Department of |
Peer Review Status | Unreviewed |
Scholarly Level | Undergraduate |
Aggregated Source Repository | DSpace |
Download
- Media
- [if-you-see-this-DO-NOT-CLICK]
- MarineDrive_McNicholl,D_2.pdf [ 346.49kB ]
- Metadata
- JSON: 1.0077962.json
- JSON-LD: 1.0077962+ld.json
- RDF/XML (Pretty): 1.0077962.xml
- RDF/JSON: 1.0077962+rdf.json
- Turtle: 1.0077962+rdf-turtle.txt
- N-Triples: 1.0077962+rdf-ntriples.txt
- Original Record: 1.0077962 +original-record.json
- Full Text
- 1.0077962.txt
- Citation
- 1.0077962.ris
Full Text
Cite
Citation Scheme:
Usage Statistics
Country | Views | Downloads |
---|---|---|
United States | 19 | 0 |
Canada | 7 | 1 |
China | 6 | 16 |
India | 1 | 0 |
Japan | 1 | 0 |
City | Views | Downloads |
---|---|---|
Ashburn | 8 | 0 |
Clarks Summit | 7 | 0 |
Vancouver | 6 | 1 |
Shenzhen | 4 | 16 |
Unknown | 2 | 0 |
Kansas City | 2 | 0 |
Redmond | 1 | 0 |
Hangzhou | 1 | 0 |
Boardman | 1 | 0 |
Guangzhou | 1 | 0 |
Tokyo | 1 | 0 |
{[{ mDataHeader[type] }]} | {[{ month[type] }]} | {[{ tData[type] }]} |
Share
Embed
Customize your widget with the following options, then copy and paste the code below into the HTML
of your page to embed this item in your website.
<div id="ubcOpenCollectionsWidgetDisplay">
<script id="ubcOpenCollectionsWidget"
src="{[{embed.src}]}"
data-item="{[{embed.item}]}"
data-collection="{[{embed.collection}]}"
data-metadata="{[{embed.showMetadata}]}"
data-width="{[{embed.width}]}"
async >
</script>
</div>
Our image viewer uses the IIIF 2.0 standard.
To load this item in other compatible viewers, use this url:
http://iiif.library.ubc.ca/presentation/dsp.18861.1-0077962/manifest